Highly renowned as the topmost manufacturer, we are gaining immense appreciation for supplying an excellent stock of Offline Boiler Chemical. These chemicals are extensively used in boilers of various processing industries. These chemicals prevents the damage of boilers caused due to corrosive chemicals. The entire stock of Offline Boiler Chemical is stringently tested on various standard quality parameters by the experts before the final dispatch in market.
- Excellent composition
- Extended shelf life
- Free from impurities
OFFLINE BOILER CLEANING CHEMICALS
Purpose of Offline Boiler Cleaning Chemical :
The primary reasons for chemical cleaning of boilers/ heat exchangers are to prevent tube failures & improve unit availability. Tube failures in low pressure boilers/heat exchangers are normally the results of creep which occurs when internal deposits produce excessive metal temperature. A relatively smaller quantity of deposit creates difficulties in high pressure boilers. Caustic corrosion & hydrogen damage, which occur only in the presence of deposits, may cause tube failures at temperatures well below the creep limit. Deposits originating both from fabrication & during operation should be considered potential problems.
All the pressure parts of steam generator may be subjected to heat treatment of some sort during fabrication or erection during forming operations, stress relief, welding or bending. Whenever carbon low alloy steels are subjected to high temperatures in the presence of air, oxidation occurs, the oxide produced is known as mill scale. Mill scale on boiler/ heat exchanger tubing is normally very thin with the exception of areas near welds & bends. Even where mill scale is initially uniform its brittleness upon cooling may produce flaking. The resulting non-uniform surface is undesirable from the standpoint of corrosion susceptibility. During operation mill scale is rapidly eroded from the steam generating surfaces & may subsequently be redeposited in critical areas. Preoperational acid cleaning removes mill scale & serves to remove atmospheric rust which inevitably accumulates to some degree during erection.
After a boiler / heat exchanger placed into service, numerous solid constituents may enter the units with the feed water & some portion of the insolubles can be expected to deposit on surfaces. If not removed these deposits accumulated over a period of time can minimize the quantity of these materials; however, complete freedom from deposition is not possible in a high pressure system. The need for occasional chemical cleaning during the life of the equipment has become a recognized fact & should be accepted as a routine maintenance practice. A frequency of service cleaning of every 3 to 4 months is recommended. This frequency should be increased if individual unit operating history dictates.
OFFLINE BOILER CLEANING CHEMICAL is designed to remove the scaling& corrosion products from boiler& cooling water circuits , heat changers etc. It is a liquid formulation to remove hardness & low concentrated silica scales that can be removed offline by circulating its dilute solution of the chemical. It is a balance formulation of Hydrochloric Acid, Dispersant Wetting Agents & Corrosion Inhibitor.
Powerful Descalent Safe For Metals Detergent Action Dosages : should be dosed in 5-10 % solution in water . warm water may be used for faster action . normally the quantity of scale required depends upon the operating condition quantity of scales and hold up.